# yd-t 1104- 2001通信用开关电源系统监控技 术要求和试验方法.pdf

展开

yd-t 1104- 2001通信用开关电源系统监控技 术要求和试验方法

1"L

中华人民共和国通信行业标准

yD/T 1104- 2001

通信用开关电源系统监控

技 术要求和试验方法

Technical Requirements&Testing Methods for Supervision Module

of T e le co mm u nic ati on SwitchP owerS upplies

2001-03-21发布2001-03-21实施

中华人民共和国信息产业部发布

YDIT 1104- 2001

目次

前言················································································。····································⋯⋯ 11

1范围·....................................................................................................................... 1

2引用标准············································································································⋯⋯ 1

3定义····································。·····。·······································································⋯⋯ 1

4要求··················································································································⋯⋯ 1

5试验方法······。··························。··········································································⋯⋯ 2

附录A(标准的附录) 通信用开关电源系统监控通信协议················································⋯⋯ 6

A1物理接口和通信方式·······················。··································································⋯⋯ 6

A2协议的基本格式·························································································⋯⋯“‘·‘二6

A3数据格式·········································································································⋯⋯ 8

A4编码表············································································································⋯⋯ 9

A5通用命令内容···································································································⋯⋯ 11

A6交流配电部分通信协议·······。·························。·····················································⋯⋯ 14

A7整流模块通信协议·································································，·····。·········⋯⋯‘·‘’·‘’·”二23

A8直流配电部分通信协议·······························································

中华人民共和国通信行业标准

yD/T 1104- 2001

通信用开关电源系统监控

技 术要求和试验方法

Technical Requirements&Testing Methods for Supervision Module

of T e le co mm u nic ati on SwitchP owerS upplies

2001-03-21发布2001-03-21实施

中华人民共和国信息产业部发布

YDIT 1104- 2001

目次

前言················································································。····································⋯⋯ 11

1范围·....................................................................................................................... 1

2引用标准············································································································⋯⋯ 1

3定义····································。·····。·······································································⋯⋯ 1

4要求··················································································································⋯⋯ 1

5试验方法······。··························。··········································································⋯⋯ 2

附录A(标准的附录) 通信用开关电源系统监控通信协议················································⋯⋯ 6

A1物理接口和通信方式·······················。··································································⋯⋯ 6

A2协议的基本格式·························································································⋯⋯“‘·‘二6

A3数据格式·········································································································⋯⋯ 8

A4编码表············································································································⋯⋯ 9

A5通用命令内容···································································································⋯⋯ 11

A6交流配电部分通信协议·······。·························。·····················································⋯⋯ 14

A7整流模块通信协议·································································，·····。·········⋯⋯‘·‘’·‘’·”二23

A8直流配电部分通信协议·······························································